The subterranean tank – an unobtrusive solution
Would you like to see as little as possible of your liquid gas tank or don’t you want to limit yourself regarding the setup of your garden? In this case the subterranean insertion of your liquid gas tank is the ideal solution for you.
The gas tank is 2,5m in length with a diameter of 1,25m. Moreover, it includes a manhole as well as a cupola and a lit made of galvanised sheet with a diameter of 90cm.
The gas tank needs to be installed in a way that the edge of the manhole cover is at least in 3m distance from all buildings, neighbouring properties, traffic and/or parking lots and from every unprofessionally maintained power source..
The costs for the construction work (digging, insertion of concrete slab, equipment of yellow sand and the covering of the tank) that need to be executed according to the rules of ITMCL 9.4 are to be paid by you. After the digging of the whole, we place the subterranean gas tank in the presence of Luxcontrol.
Technical documents for installers
The aboveground liquid gas tank – easy and fast setup
The aboveground installation of your liquid gas tank is optimal, if you have enough space in your garden. The installation is feasible with a minimum of construction work to be done, which is very cost-effective.
The tank is 2,5m long with a diameter of 1,25m and is painted in RAL-white.
It is possible to install the tank on a 2,50 x 1,50m concrete slab. However, the gas tank needs to maintain a distance of 5m from all buildings, 3m from all neighbouring properties, traffic and/or parking lots and from every unprofessionally maintained power source.